The Royal Melbourne Hospital
The Royal Melbourne Hospital is a large public hospital with over 500 beds and a significant teaching component.
System Size2 x 100 Amp Active Harmonic Filters
Key EquipmentActive Harmonic Filter
Harmonic interference was detected in close proximity to the ECG equipment in the new outpatient’s wing. This interference put the ECG test results into question and caused the ECG test area to be temporarily closed.
Part of the hospital and an important patient service was closed.
Initially, we carried out a power quality audit. We found that the ECG interference was coming from the main supply cable which carried a high level of third harmonic current. 2 x 100 amp Active Harmonic Filters were installed and programme
The hospital was able to reopen the ECG test area and continue its important, lifesaving work.